June 12, 2015 | Bretislav Valek
The Reliance SCADA/HMI system is used at Nippon Express's production plant and warehouse in the Dutch city of Rotterdam to visualize and control the process of cold/heat storage in subterranean wells. Up to three well systems, each of which consists of one cold well and one hot well, can be controlled.
If a higher system is asking for heat, water is pumped from the hot well through a heat exchanger where it is cooled by a heat pump and injected into the cold well. In the summer, cooling is demanded and water is pumped from the cold well into the hot well with extra heat added by a dry cooler equipped with fans. The condensing side of the heat pump increases the water temperature feeding the building.
A Climatix POL638 controller by Siemens is used as the control system. For communication between the higher system and the Climatix controller, the BACnet protocol is used. Alarms and requests are communicated through the BACnet interface. For communication with the Reliance system, the OPC standard is used.
Every month, the controller calculates all energy stored in or taken from the wells. When a new year starts, a report is automatically generated by Reliance (an Excel template filled with data) and then automatically sent to the email addresses provided on the Settings page.
The entire system had to be registered to obtain government licenses for storing energy in wells.
Try the Reliance SCADA/HMI system on several example projects or download the installer of the trial version for free.
Visualization and control of the cooling and heating system at Nippon Express's production plant and warehouse in Rotterdam
1 x Siemens Climatix POL638
1 x Reliance 4 Control with 10,000 data points